Sinumerik Alarm 14800 Channel %1 block %2 programmed path speed less or equal to zero
%1 = Channel number
%2 = Block number, label
A negative F value has been programmed in conjunction with the G functions G93, G94, G95 or G96. The path velocity may be programmed in the range 0.001 to 999 999.999 [mm/min, mm/rev, deg/min, deg/rev] for the metric input system and 0.000 1 to 39 999.999 9 [inch/min, inch/rev] for the inch input system.
– Correction block is reorganized.
– Interface signals are set.
– Alarm display.
Program the path velocity (geometric sum of the velocity components of the geometry axes involved) within the limits given above.
Clear alarm with NC START or RESET key and continue the program.
- Siemens Diagnostics Guide by Siemens